! This version of Internet Explorer is not supported anymore !
We recommend to visit our website with another browser (Microsoft Edge, Chrome, Firefox, ...)
We recently changed our 45x45 metal bases with claws for switching material: these will be available without elastic bands between the claws from now on.
This is to ensure a smoother installation.
The attached drawings show how you can push the loose claws back into their snap position.
If the push buttons and the staircase timer are connected with a 2-wire connection, the total working current of the LEDs may be sufficiently high to have its coil be constantly activated.
Adjust the wiring to a 3-wire connection. OR Replace the LEDs with neon lamps (only in push buttons with an E10 lamp base).
Specific products are needed, as this type of load type has a high starting current, which the product must be able to handle for a long period of time. Legal provisions also prohibit the use of just any light dimmer.
This website makes use of the following types of cookies: